steam generator. (3) The term "steam generator" is more accurate than the when the substance is above its critical pressure, which is more familiar term "boiler." There is no fluid boiling 3208.2 psia for water. Above the critical pressure the water changes from a
= Specific Volume of the air at the pipe inlet during cleaning (m3/kg) = Specific Volume of the system fluid of the pipe inlet generating boilers, steam heat exchangers, steam turbines or other steam lines. The purpose of steam blowing is to dislodge
High-Flow Steam Condensate Pumps with Tank. Move a higher volume of condensate than standard steam condensate pumps. Use these pumps in low-pressure steam systems to capture hot condensate and return it to your boiler or feed unit. They turn on when the tank is 2/3 full and turn off when condensate drops to 6" deep. Max.
6.1 Feed Water (FW) System. Feed water can be defined as return condensate + make up water. Feed water is the high-pressure deaerated (removal of gases such as oxygen and carbon dioxide) water supplied to the boiler from which steam is generated. In the case of SC or USC boilers, the feed water has additional significance.